0061 RF Occupancy Or Vacancy Sensor Person Manual Lutron Electronics
Seek advice from that product’s set up sheet for directions. Twist and remove mounting bracket to insert battery. Product Description Lutron’s ceiling-mounted Occupancy Sensors are wireless, battery-powered, passive infrared (PIR) units that automatically control lights via RF communication with a dimming or switching gadget. These Sensors detect the heat from individuals shifting within an space to find out when the house is occupied. The Sensors then transmit the suitable commands to the associated dimming or switching device to show the lights on or off robotically, providing each convenience and distinctive power financial savings. Sensor does not perform satisfactorily from this location, it may be moved to 1.4 Ifanother location by pulling the Sensor straight down and repeating steps 1.3 and 1.4. 1.5 If the Sensor’s performance is passable, it must be completely hooked up to the ceiling tile, as described in section G. Everlasting Mounting. Short-term Stable Ceiling Mounting Use this procedure if the Sensor will be mounted on a stable, steady ceiling surface comparable to drywall, plaster, concrete, or wooden. Two 3M™ Command™ adhesive strips are supplied for quickly mounting and testing the Sensor on easy, solid ceiling surfaces. These strips are designed for easy, damagefree elimination and aren't reusable. These strips should not be used for completely mounting the Sensor (see part G. Everlasting Mounting ). Fastidiously observe the elimination instructions below to make sure the ceiling shouldn't be broken during elimination. Observe: Don't use the adhesive strips on ceiling tiles, as they are going to possible cause harm to the tile upon removing. Simple-to-follow Instructions Set-Up In order for the Sensor to operate correctly, it must first be arrange with a corresponding dimming or switching system. The process for establishing a Sensor with a Maestro Wireless® (MRF2- only) Dimmer or Digital Swap is detailed under. P/N 041-172a 2.1 Peel the pink "Command Strips" liner off of one of many adhesive strips and apply the strip to the flat aspect of the mounting bracket as shown within the diagram. Be aware: Do not cover the bracket’s screw holes because they will be used to mark screw gap places on the ceiling. Organising a Sensor with a Maestro Wireless Dimmer or Digital Swap Dimmer Key Options · Low Maintenance. 10-yr battery life. Handy low-battery indicator. · A number of Devices. Up to three Sensors can work collectively to regulate lights for broader coverage in massive spaces. Each Sensor could also be added to as much as 10 receiving units. Sensor Operation Occupancy Version - The Sensor will robotically turn the lights on when the house is occupied and automatically turn the lights off after the area is vacated. The Sensor will automatically turn the lights off after the space is vacated. There's a constructed-in 15-second vacancy grace interval that begins when the lights are automatically turned off, throughout which the lights will mechanically turn back on in response to movement. This grace period is provided as a security and convenience feature within the occasion that the lights flip off whereas the room is still occupied, so that the consumer doesn't must manually turn the lights back on. After 15 seconds, the grace period expires and the lights have to be manually turned on. This Sensor is part of a system and can't be used to manage a load and not using a suitable dimming or switching gadget. Seek advice from the instruction sheets of the receiving machine(s) for installation data. The Sensor may be installed as much as 60 ft (18.3 m) away from the associated dimming or switching gadget(s) if they're in direct line of sight. If there are walls or other barriers between the Sensor and receiving gadget(s), the Sensor must be positioned inside 30 ft (9.1 m). Caution: This product should not be used to control tools which could create hazardous situations, similar to entrapment, if operated accidentally. Sensor in a location the place it has a broad view outside the supposed area. If this is unavoidable, the lens could be masked to dam the view of undesired areas (consult with section I. Lens Masking). This warranty is in lieu of all different specific warranties, and the implied guarantee of merchantability is restricted to 1 year from purchase. This guarantee doesn't cover the price of set up, removal or reinstallation, or injury resulting from misuse, abuse, or injury from improper wiring or installation. This warranty does not cowl incidental or consequential damages. LUTRON’S Liability ON ANY Claim FOR DAMAGES ARISING OUT OF OR IN CONNECTION WITH THE MANUFACTURE, SALE, Set up, Delivery, OR USE OF THE UNIT SHALL By no means EXCEED THE PURCHASE Worth OF THE UNIT. This warranty gives you particular authorized rights, and it's possible you'll have other rights which range from state to state. Some states don't allow the exclusion or limitation of incidental or consequential damages, or limitation on how lengthy an implied guarantee may last, so the above limitations might not apply to you. Patents pending. Lutron, Maestro Wireless, and the Sunburst logo are registered trademarks and Radio Powr Savr is a trademark of Lutron Electronics Co., Inc. ANSI is a registered trademark of the American National Requirements Institute. IEC is a trademark of the International Electrotechnical Fee. Made and printed within the U.S.A. 25/09/09 P/N 041-172 Rev. A 8 ft (2.4 m) 18 x 18 ft (5.5 x 5.5 m) 13 ft (4.0 m) 9 ft (2.7 m) 20 x 20 ft (6.1 x 6.1 m) 14.5 ft (4.4 m) 10 ft (3.0 m) 22 x 22 ft (6.7 x 6.7 m) sixteen ft (4.9 m) 12 ft (3.7 m) 26 x 26 ft (7.9 x 7.9 m) 19 ft (5.Eight m) Temporary Mounting Methods 1.1 1.2 Insert the ceiling tile mounting wire through the 2 smaller holes within the mounting bracket and change the mounting bracket. Mount Sensor to a ceiling tile by inserting the wire legs by the tile, ensuring the Sensor is flush to the tile. Note: Don't twist wire legs together. 1.2 After the Sensor has been briefly mounted, depart the Sensor in place on the tile and both take the tile down or remove an adjacent tile to achieve entry to the legs of the mounting wire on the back of the tile. Low Activity: That is probably the most delicate setting and can detect very slight motions. This is the beneficial setting, as it will work effectively for practically all functions. It is ideal for areas the place occupants will typically be seated for lengthy durations of time. Twist the wire legs collectively tightly so the mounting bracket remains snug towards the tile. This setting is slightly less delicate than the Low Activity setting and can be utilized for spaces that expertise normal exercise. This is the least delicate setting and can be utilized for areas that may generally solely experience massive motions, corresponding to foot site visitors. The Low Activity setting is the default and will perform best for most functions. Rarely, if the Sensor is positioned near exterior noise sources comparable to heating vents, air conditioning vents, or gentle bulbs, it may flip the lights on with out occupancy or keep the lights on too lengthy after vacancy. If this occurs, altering the sensitivity to Medium Exercise or Excessive Exercise should resolve the issue. Exchange the tile. Everlasting Strong Ceiling Mounting 2.1 2.2 2.3 Advanced Set-Up Operation The advanced set-up is accessed by using the buttons on the back of the Sensor. Drill two 3/16 in (4.6 mm) pilot holes for the provided screw anchors. Press the anchors into the holes and tap flush with a hammer. To display the current setting, press and launch the specified button. An LED will illuminate briefly, indicating the current setting. Place the flat aspect of the mounting bracket against the ceiling and install the 2 provided screws using a hand screwdriver. To regulate a setting, press and hold the specified button until the LED corresponding to the present setting begins flashing rapidly, indicating the setting can now be adjusted. Every subsequent button press of less than 2 seconds will increment the mode to the following accessible setting. Urgent any of the opposite buttons will don't have any impact. To save lots of the selected setting, press and hold the button till the LED turns on stable, indicating the saved setting. In the course of the adjustment process, if there isn't any exercise for 30 seconds, the LEDs will turn off and no settings can be saved. Note: Don't over-tighten. 2.4 Attach the Sensor to the mounting bracket by inserting and twisting in a clockwise path till the Sensor locks into place. To take away the bracket from the ceiling, grasp the removing tab on the adhesive strip and pull the tab VERY SLOWLY straight throughout the ceiling, stretching the strip till the bracket releases from the ceiling. Discard the strip. Never pull the strip at an angle, as it might break or damage the ceiling floor. Be aware: Do not pull at an angle. Lens Masking (Non-compulsory) Every time possible, the Sensor needs to be installed in a location where it cannot easily see into areas outside the supposed space, reminiscent of hallways or adjacent rooms. If this case can't be avoided, portions of the lens may be masked with the supplied labels to block the Sensor’s view of the undesired areas. It is strongly recommended to take away the Sensor from the mounting bracket before making use of Advanced Set-Up (Optionally available) the masking labels. The Sensor features a number of superior set-up modes. For the vast majority of installations, the default settings will present the perfect efficiency and also you will not must utilize the superior set-up. The Occupancy version of the Sensor has three adjustable advanced set-up modes: Timeout, Auto-On, and Sensitivity. The Vacancy-Only model has only two modes (Auto-On not out there). The default settings are listed under. The Sensor could be screwed onto the mounting bracket in several totally different orientations. Be sure to note the Sensor’s orientation before taking it down and exchange the Sensor in the same orientation to ensure the supposed area will get blocked. Outer lens sections correspond to the detection areas furthest away from the Sensor, while interior sections correspond to areas closer to the Sensor. Watch out when applying the labels to avoid creating gaps between adjacent masked sections. The Sensor might detect movement by means of inadvertent gaps. All the time (Occupancy model only) Timeout 30 min 15 min 5 min Auto-On Always Low light Disable Exercise Timeout 30 min 15 min 5 min Advanced Set-Up Modes Auto-On All the time Low mild Disable Activity Exercise: Low Exercise Lens sections shown in white are masked with labels Timeout The Sensor will turn the lights off if no motion happens in the course of the timeout interval. There are three out there timeout settings: 5, 15, and 30 minutes. Lens Mask Lens sections proven in gray have not been masked Auto-On The automatic-on performance of the Sensor can be adjusted to control how the lights respond upon initial occupancy. There are three out there settings: Always, Low gentle, and Disable. At all times: The lights will at all times turn on. Testing Sensor Coverage With the Sensor mounted on the ceiling, press and release the "Test: Sensor" button on the entrance of the machine. The lens will glow briefly, indicating the check mode has been entered. Be aware: There is a heat-up interval of roughly forty seconds after the batteries are installed earlier than the take a look at mode could be activated. If the button is pressed during this time, the lens will flash continuously till the heat-up interval is full, and then the check mode will likely be automatically entered. Affirm the coverage space by strolling via the house and observing the lens. The lens will glow stable each time motion is detected. If the lens remains off throughout motion, the Sensor cannot detect motion at that location. Press and release the "Test: Sensor" button again to exit the check mode. If the button is just not pressed, the check mode will mechanically time out 15 minutes after being enabled, or 5 minutes after the last detected motion if the room is vacated. If the Sensor has significant bother detecting movement in the course of the take a look at, it needs to be moved to another location and retested. If the Sensor nonetheless has poor detection from the new location, refer to the Troubleshooting part. Non permanent Drop Ceiling Mounting Use this procedure if the Sensor will probably be mounted on a ceiling tile. The ceiling tile mounting wire is supplied for each non permanent and permanent mounting of the Sensor to drop ceilings composed of a number of tiles. It is designed to permit short-term mounting, testing, and repositioning (if crucial) of the Sensor without damaging a ceiling tile. Once the Sensor’s closing place has been chosen, the mounting wire can be twisted to lock the Sensor in place completely. If the Sensor protection and wireless communication checks have been successfully completed, use the mounting bracket as a template to mark the screw gap locations with a pencil. Observe: Pull very slowly. Max. Room Dimensions Radius of Coverage for Full Protection at Flooring If you are unsure about accurately positioning the Sensor, the following temporary mounting and testing procedures are really useful to verify proper performance before permanently installing the Sensor. Sensor’s detection range depends on the ceiling top, as shown within the desk below. Discover: Don't disassemble, crush, puncture, or incinerate the batteries. Don't dispose of batteries in regular household waste. Please recycle, take to a proper battery disposal facility, or contact your local waste disposal provider relating to native restrictions on the disposal or recycling of batteries. O NOT mount the Sensor within four ft (1.2 m) of HVAC vents or gentle bulbs installed below the ceiling line. Hotter rooms could reduce the Sensor’s potential to detect occupants. Use solely excessive-high quality lithium batteries, dimension CR123, three V (ANSI-5018LC, IEC-CR17345). Do not use rechargeable batteries. Utilizing improperly rated batteries might damage the Sensor. For questions concerning the installation or operation of this product, call the Lutron Technical Assist Heart. Please provide actual model quantity when calling. U.S.A. and Canada (24 hrs / 7 days) Setting the Occupancy Gentle Degree (occupancy model, dimming devices solely) the Sensor to the mounting bracket by inserting and twisting in a clockwise 2.5 Attach direction till the Sensor locks into place. Sensor protection and wireless communication exams as described in 2.6 Carry out sections E. Testing Sensor Protection and F. Testing Wireless Communication. The Sensor must be installed in a location the place it has a great view of all elements of the room. The Sensor requires line of sight to function properly. If you can not see the Sensor, it cannot see you. The Sensor can't see through glass objects comparable to patio or shower doorways. The range and performance of the RF system is very dependent on quite a lot of complicated components such as: · Distance between system parts · Geometry of the constructing construction · Construction of partitions separating system components · Electrical gear situated near system elements Technical Help 2.2 Identify a location on the ceiling the place the Sensor can have an excellent view of the room. 2.Three Remove the black "wall side" liner from the adhesive strip. The Sensor is designed for ceiling use solely. Do not set up on ceilings larger than 12 ft (3.7 m) or non-ceiling surfaces. Doing so could significantly inhibit the Sensor’s performance. 4. Do not paint Sensor. · · · · The "Lights On" and "Lights Off" buttons should now switch the lights in the room on and off, respectively, when pressed. Repeat the above process to arrange the Sensor with any extra devices. The Sensor is meant for indoor use only. Operate between 32 °F and 104 °F (0 °C and forty °C). 1.1 a number of seconds. Sensor that has been arrange. After approximately 6 seconds, the lens will flash rapidly several occasions, indicating the sunshine stage has been saved. All Sensors arrange with the Dimmer will now use the saved occupancy mild stage. 2. Clear Sensor with a gentle damp cloth solely. Do not use any chemical cleaners. Be aware: This gear has been examined and located to comply with the boundaries for a category B digital device, pursuant to half 15 of the FCC rules. These limits are designed to supply reasonable safety against dangerous interference in a residential installation. This equipment generates, makes use of and might radiate radio frequency energy and, if not installed and utilized in accordance with the instructions, could cause harmful interference to radio and tv reception, which might be determined by turning the gear off and on. The user is encouraged to attempt to correct the interference by one or more of the following measures: Reorient or relocate the receiving antenna. Enhance the separation between the gear and receiver. Connect the tools into an outlet on a circuit completely different from that to which the receiver is related. Seek the advice of the vendor or an experienced radio/Television technician for help. Warning: Adjustments or modifications not expressly authorized by Lutron Electronics Co. might void the user’s authority to operate this gear. This system complies with Part 15 of the FCC rules. This gadget should settle for any interference obtained, together with interference that will cause undesired operation. Swap 2.1 Set the Dimmer to the desired mild stage for coming into the room. 2.2 Save holding the "Lights On" button on the entrance of a Word: For both Sensor model, the lights will also be manually turned off at any time through the use of the dimming or switching device straight. Vital Notes or Add the Sensor to the Dimmer or Swap by pressing and holding the "Lights Off" button on the front of the Sensor for approximately 6 seconds till the lens flashes briefly. The lights within the room will even flash 3 occasions, indicating the Sensor has been efficiently added. The Dimmer or Switch will exit set-up mode automatically. The sensitivity of the Sensor may be adjusted primarily based on the expected stage of exercise throughout the room. There are three obtainable exercise settings: Low Exercise, Medium Exercise, and Excessive Exercise. Permanent Drop Ceiling Mounting Observe: Leave the removing tab uncovered past the sting of the bracket so it can be accessed for elimination later. 6 seconds until all LEDs on the machine start flashing. Release the tap button. Sensor is detecting motion in areas that aren't desirable, equivalent to hallways or adjacent rooms, consult with section I. Lens Masking. If Sensor detection is passable during this check, perform the wireless communication take a look at as described in section F. Testing Wireless Communication. Testing Wireless Communication This test ought to be carried out to verify that the Sensor has been correctly arrange with the corresponding dimming or switching machine and that there's proper wireless communication from the chosen Sensor location. If the lights in the room aren't on, flip them ON manually at the dimming or switching device. Press and release the "Lights Off" button on the front of the Sensor. The lights ought to flip OFF. Press and launch the "Lights On" button on the entrance of the Sensor. The lights should activate. If the lights don't respond accurately, consult with the Troubleshooting part. Low gentle: The lights will solely turn on automatically upon entry if there isn't already ample ambient mild in the room. Hallway falls inside Sensor’s protection area. Disable: This setting converts the Sensor to vacancy mode. The lights will not routinely activate however will still mechanically turn off after vacancy. The lights should be manually turned on by utilizing the associated dimming or switching machine. Note: The 15-second vacancy grace interval is energetic on this mode. Check with the Sensor Operation section at the beginning of this doc for more details. Troubleshooting Symptom Doable Causes Answer Lights don't activate when area is occupied. Sensor is not correctly added to dimming / switching system(s). Sensor’s Auto-On setting is ready to "Low light" or "Disable". The lights had been lately turned off manually and the timeout has not yet expired. Sensor doesn't have full view of room. Sensor is outside wireless vary of dimming/switching machine. Refer to part B. Set-Up. Confer with part H. Advanced Set-Up. Dimming/switching machine has been improperly wired. Mild bulb(s) burned out. Breaker is off or tripped. Sensor’s timeout is just too quick for this application. Sensor doesn't have full view of room. Lens mask is improperly utilized. Sensor’s sensitivity is just too low. Sensor’s timeout has not but expired. An external noise supply similar to an HVAC vent is interfering. Seek advice from part A. Pre-Installation. Habits of lights does not match Sensor settings. Sensor protection extends past room perimeter. The intended setting was not saved. A number of Sensors are added to a dimming/switching gadget and their settings don't match. Confer with part A. Pre-Set up. Check with part C. Sensor Placement or I. Lens Masking. Seek advice from part H. Superior Set-Up. Seek advice from section H. Advanced Set-Up. Sensor lens doesn't glow in response to movement throughout Sensor coverage testing. Sensor can't see movement on account of obstruction. Room is too big or oddly formed. Transfer Sensor to a different location. Seek advice from part C. Sensor Placement. Multiple Sensors could also be necessary for full room coverage. Strive transferring Sensor to a new location or decreasing sensitivity. Refer to section C. Sensor Placement or H. Advanced Set-Up. Lights turn OFF while space is occupied. Lights stay ON after house is vacated. Lens does not stop glowing during Sensor coverage testing even when there isn't a movement. Lights don't respond accurately during wireless communication testing. Sensor lens flashes and lights do not turn on when area is occupied. Battery has been installed incorrectly. An external noise source equivalent to an HVAC vent is interfering. Check with part C. Sensor Placement. Refer to section C. Sensor Placement or F. Testing Wireless Communication. Discuss with part H. Superior Set-Up. Seek advice from part C. Sensor Placement. Discuss with part I. Lens Masking. Consult with section H. Advanced Set-Up. Check with section H. Advanced Set-Up. Try shifting Sensor to a brand new location or decreasing sensitivity. Check with section C. Sensor Placement or H. Advanced Set-Up. Sensor will not be appropriately added to dimming / switching gadget. Sensor is outside wireless range of dimming/switching device. Refer to section B. Set-Up. Move Sensor nearer to dimming/switching gadget and retry take a look at. Refer to part F. Testing Wireless Communication. Battery has been put in incorrectly. Dimming/switching device has been improperly wired. Light bulb(s) burned out. Breaker is off or tripped. Battery is low. Refer to section A. Pre-Set up. Remove sensor from test mode. Check with part E. Testing Sensor Protection.